Working power: A CR17335/17450 lithium manganese battery
B 2* AA alkaline battery
Maximum Alarm Current (LED on): ≤100mA@3VDC
Operating Humidity Range: ≤95%RH(40°C±2°C) Relative Humidity, Non-condensing
Operating Temperature Range: -10°C to 50°C (14°F to 122°F)
Fix temperature Alarm: 57°C (135°F) A1R
Rate of rise Alarm: 7.1°C/5S A1R
Wireless working frequency band: 428-438MHZ
Wireless transmit power +20DB
Alarm level: ≥85db /3m
Height: 54.5mm installed in Base
Diameter: 126.7 mm
INSTALL THE DETECTOR BASE
A. Open area smoke or heat detectors are intended for mounting on a ceiling or a wall in accordance with the fire standard in your country.
B. Attach mounting base to ceiling or wall.
INSTALL THE DETECTOR HEAD
A. Align detector head alignment mark line with the base’s start alignment mark line.
B. Push the detector head into the base while turning it clockwise to secure it in place.
C. Do not install the detector head until the area is thoroughly cleaned of construction debris, dusts, etc.
D. Test the detector(s) as described in the TESTING section of this manual.
|Installation Mode:||Ceiling Mounted|